DSC - Amer-x Security The sections that follow describe additional requirements for the type of installation (for example, Central Station Fire Alarm systems, Local Protected Fire Alarm systems, and so on). All field wiring must be 18-gauge or larger (for example, 16, 14, and so on). Use UL listed smoke detectors compatible with the Refer to Appendix A. Follow the current load restrictions shown in Section The Model 5220 Direct Connect module must be installed (see Section 4.7 for wiring) Requirements for Remote Station Protected Fire Alarm Systems, for Dital Communication or Polarity Reversal 1. V7.2VA-CC, 12V 7.2VA hh efficiency level IV transformer for DSC MD-12. English, French and Spanish instructions. 188, KIT16-120ADTNT, ADT Dealer program kit. 282, PC4020-XFRM, 120V 60 Hz transformer for PC4020CF.
ACE Security Systems Downloads The following applicable NFPA 72 standards can be found in more detail in the NFPA 72 National Fire Alarm Code, 1993 Edition: Chapter 3 ï Local Protected Fire Alarm Systems, Chapter 4 Chapter 4 ï Central Station Fire Alarm Systems ï Auxiliary Protected Fire Alarm Systems for Fire Alarm Service (City Box) ï Remote Station Protected Fire Alarm Systems (Polarity Reversal) ï Proprietary Fire Alarm Systems Requirements for All Installations General requirements are described below. See Section Agency Listings and Requirements Requirements for Auxiliary Protected Fire Alarm Systems for Fire Alarm Service 1. Security systems, CCTV systems, and fire system user manuals. DSC Alexor, Power Series, Escort & Maxsys. Alexor 9155 · DLS System.
Loading. - Lista de Precios - Corporativo Inalarm Contents Section 1 Introduction About This Manual Optional Accessories Section 2 Agency Listings and Requirements Federal Communications Commission (FCC) Underwriters Laboratories (UL) Requirements for All Installations Requirements for Central Station Fire Alarm Systems Requirements for Auxiliary Protected Fire Alarm Systems for Fire Alarm Service Requirements for Remote Station Protected Fire Alarm Systems, for Dital Communication or Polarity Reversal California Fire Marshal (CFM) Factory Mutual (FM) Materials and Equipment Board of Acceptance Division (MEA) Section 3 Control Panel Installation Electrical Specifications Environmental Specifications Wiring Specifications Model 5207 Wiring Diagram Current Draw Worksheet Worksheet Example Worksheet Requirements Power Supply Wiring Connecting the 5198 to AC Power Connecting the 5198 to Batteries Mounting the Terminal Strip Description Telephone Line Connection Cable Connectors Section 4 Compatible Product Installation Class A (Style D) Zones Class B (Style A) Zones Four-Wire Smoke Detector Connection Two-Wire Smoke Detector Connection Model 4180 Status Display Module Model 5210 Zone Expander Wiring Model 5220 Direct Connect Module City Box Connection NFPA 72 Polarity Reversal Keltron 95M3158 Tones Transmitter Module Model 5230 Remote Annunciator Setting ID Codes i Model 5207 Fire Control/Communicator Installation and Operation Manual Permanent Connection Mounting the 5230 Remote Annunciator Temporary Annunciator Connection Model 5395 Snal Power Expander Model 7181 Zone Converter Supervised Notification Appliance Outputs Auxiliary Relays Section 5 Operation Built-in Touchpad and Model 5230 Operation Built-in Touchpad Display Codes LED Indicators System Testing Fire Drills Walk Test (Mode 22) Automatic Self Test Watchdog Circuit Section 6 Programming: Quick Reference Section 7 Programming: Step-by-Step Complete Reference Using Step Programming Programming Examples Step Programming Options Step 1. 2.3 California Fire Marshal (CFM) The CFM approval number for the 5207 is : Factory Mutual (FM) The Model 5207 is FM approved under project # OQ1A3. IT-100, Serial Integration Module for DSC PowerSeries Control Panels. 146, PC1404PCBSPA, PC1404 PCB only, 1 Installer manual per.
PC4010 / PC4020 - Elvey Security Technology Follow the current load restrictions shown in Section Use the 5207ís built-in dialer or install the Model 5220 Direct Connect Module (see Section 4.7). Zone expansion simple using DSC addressable devices. each - home-run wiring is eliminated and the installation is simplified for the installer. PC4020CF.
PC4820 datasheet - Warning This device has been verified to comply with FCC Rules Part 15. Programming is maintained in the PC4820's non-volatile memory. PC4010, PC4010CF, PC4020, and PC4020CF control panels. installation manual.
Control Panels D9412GV3/D7412GV3/D7212GV3. UL Installation. If the 5207 and its accessories are to be used as part of a UL installation, carefully read the UL requirements in this section. The Ground Fault Detection option must be selected (programming Step 5). The Phone Line #2 Enable option must be selected (programming Step 9). The Phone Line Monitor Enable option must be selected (programming Step 9). Set the Total Attempts option for between 5-10 attempts (programming Step 10). Do not select the Ground Start Option (programming Step 9). Enable the automatic daily test by selecting a phone number for the Report Test to Phone #1-4 option (programming Step 14.4). On class A (style D) zones, the number of waterflow devices is limited to five. Auxiliary relays may not be programmed to activate for Pre-Alarm. Control Panels D9412GV3/D7412GV3/D7212GV3 en UL Installation Instructions Control Panels Table of Contents en 3 Table of Contents 1 Installation.
Dsc pc4020cf programming manual:
Rating: 90 / 100
Overall: 100 Rates